When it comes to safety we share all of our best practices with anyone that would like to learn.
The very first Novinium Value is Safety. It states:
“Safety is our first priority. We provide an ever–improving safe work environment for our team members, our customers, and the public.”
The greatest safety risk we face is electrical contact. We can be safe from all known electrical hazards if we follow the 10 Commitments of Electrical Safety. If you ignore one or more of these commitments, you are not welcome on our team because you will endanger your life and the lives of others.
Before the 10 Commitments are revealed to us we should understand the following defined terms:
Any injection equipment that is physically connected to any energized or potentially energized electrical cable or equipment. This includes but is not limited to:
Never proceed without a clear and accurate understanding of the circuit.
Never proceed without clear and accurate switching instructions.
Never deviate from the prescribed instructions without authorization from the Switching Authority.
Everyone on the job site must discuss and understand the work and switching plan for the day. If the plan(s) change, stop work, revise, and document a new plan for the balance of the work.
Check your gloves, footwear, hot sticks, electrical testing devices, dielectric blankets/barriers, hardhat, eye- and face protection, grounds, AED, and first aid equipment.
Always provide warning, receive a facsimile reply of the warning, and provide an Affirmative Acknowledgement when de-energizing, grounding, and switching equipment.
Wherever possible and allowable, de-energize and ground cables and equipment to Best Available Ground before performing any work within a 4 foot zone.
Never use your hands to manipulate any energized or potentially energized equipment. Always wear Dielectric Gloves when using a hot stick.
Wear rubber within 4 feet of an Uncovered Zone. Never let any part of your body or a conductive tool you are holding (i.e., anything other than a hot stick or suitably rated dielectric tool) into an Uncovered Zone without wearing the appropriate PPE.
Starting only from an energized state, always test to confirm a de‐energized state and ground to the Best Available Ground the cable or equipment to that you will be touching without wearing dielectric gloves. Examples where it is necessary to touch cables or equipment without wearing dielectric gloves include changing elbows, installing IAs, performing TDR and RF location testing, and changing splices.
Cover all exposed Energized or Potentially Energized equipment. Place cover-ups so that all required work can be performed without breaking the plane of the cover-ups with any tool or body part, whether or not the body part is Rubbered-Up (See Commitment 6). If it is not possible to apply covers, de-energize the equipment. Document the cover-up together with Commitment 9 – Isolation from Ground with an As Isolated Photograph and record in Knomentous. Note: For equipment with more than a single termination, there is one As Isolated Photograph for each cable subsegment entering the equipment on which we work.
The operator(s) and any equipment being used by the operator(s) are separated from ALL Ground Potential by a Substantial Dielectric Barrier rated at or above line voltage or at least two times the Minimum Approach Distance (MAD). De-energize the equipment if it is not possible to apply ground covers. Document the Isolation from Ground together with the Commitment 8 – Cover Up with an As Isolated Photograph and record in Knomentous. Note: For equipment with more than a single termination, there is one As Isolated Photograph for each cable subsegment entering the equipment on which we work.
Before spiking and cutting a cable always install at least one temporary ground. The condition of the neutrals on aged bare concentric neutral cables is uncertain; jacketed cables may have no exposed neutrals; unshielded cable have no neutrals. For the spiking and cutting steps which follow, the spiking tool and cutting head must be connected in parallel to the Best Available Ground and the temporary ground. If the Best Available Ground is a temporary ground, two temporary ground rods shall be utilized.
Spike a cable on which the conductor is not visibly grounded before cutting it behind a Substantial Barrier.
Cut spiked cables remotely with a grounded cutter. Cut the cable while standing more than 8 feet from the cut location.
A Substantial Barrier must be between the cut and all personnel.