Diagnostic Testing of Stochastic Circuits
Electrical Insulation Conference and Electrical Manufacturing Expo
By G.J. Bertini
October 22, 2007
The desire of circuit owners to prioritize their underground cable rehabilitation expenditures has spawned a variety of diagnostic testing tools. The goal of these diagnostic tests is to separate the “at risk” cable population into the subsets of those that are likely to provide reliable service for some time and those that are likely to fail first – the “good” from the “bad.” A decade of field failure data, covering over 18,000 km of cable installed over the 3 decades between 1969 and 1999 examined in this paper, provide statistically significant insights into the stochastic nature of cable reliability. A low cost method to prioritize circuit rehabilitation efforts is described. The method provides the foundation for the economic modeling and optimization of various rehabilitation strategies.
- Economic considerations before applying diagnostic testing
- Thermodynamic considerations before applying diagnostic testing
- Crow-AMSAA statistics provide inexpensive way to make informed strategic funding decisions for aging underground infrastructure
- Predict future underground cable failures to target the least reliable cables for rehabilitation
- Compare diagnostic testing economics against rejuvenation, replacement, or repair
Please enter your information below to view this content.